Viqua (Trojan) UVMax Sleeve for Models G, G+ & Pro 10 - # 602974
Viqua UVMax #602974 Sleeve
You save: $14.00!!
Found a Lower Price? We price match comparable systems!
Request a Price Beat
Guaranteed Genuine Trojan UVMax #602974 Original Equipment Sleeve. Don't be Fooled by Knock-Offs!
- Related Products
- Installation / Manual
- Why Genuine
We are pleased to offer a complete selection of replacement quartz sleeves for all Viqua (Trojan) UVMax ultraviolet (UV) sterilizers.
Viqua (Trojan) UVMax Model #602974 replacement sleeves are designed only for use in Viqua (Trojan) UVMax UV sterilizers. We do not recommend that you attempt to use Trojan replacement sleeves in models made by other manufacturers.
It is critical that only genuine UVMax brand original equipment sleeves be used in your system. It has come to our attention that a number of Chinese manufacturers are making knock-off replica UV sleeves. While they may physically fit in a UVMax system, they are NOT compatible. Testing of a wide range of these sleeves has shown that many do not allow a safe UV dose to pass through the sleeve and may be subject to failure.
UVMax #602974 is the sleeve for the following models:
UVMax #602974 Specifications
|Replace Sleeve||every 24 Months or as needed|
How to change a UVMax #602974 Sleeve
- Turn off water supply valve to UV sterilizer
- Turn on faucet elsewhere in the home to depressurize the system
- Disconnect your UV system from power (unplug unit)
- Allow system to cool for 5 - 10 minutes
- Follow instructions for removing lamp
- Remove the top retaining nut & O-ring
- Remove the bottom retaining nut, Spring and loosen the O-ring to drain the water
- Remove the quartz sleeve from the UV chamber.
- Clean the quartz sleeve with a cloth soaked in CLR, vinegar or some other mild acid and then rinse with water.
- Re-insert the quartz sleeve with O-ring(s), Spring, and retaining nut(s).
- Hand tighten the retaining nut(s), taking care not to over-tighten.
- When service is complete, assemble the prerequisites in the reverse order of disassembly.
- Turn on water supply valve
- Check for leaks
- Close faucet elsewhere in the home
Viqua UVMax #602974 Sleeve Reviews
Ordered our new UV water treatment lamps from this company. Great product knowledge and excellent customer service, quick shipping and fair pricing. Highly recommend Home Plus Products! - Tye O
Viqua replacement pack for UV lamp and cylinder
Complete package for Viqua UV system came promptly and intact. Made maintenance of system simple and complete. Best prices and support also from the company since original purchase and installation of my home water system! - Blair Ota