Excelight EL1129L Lamp
Excelight EL1129L Replacement UV Lamp
Our Price: US$77.95
You save: $23.73
Write a review.
Found a Lower Price?
Request a Price Beat
Lowest Price Guaranteed!If you find a lower price on this product call us or Click here to request a price beat.
Guaranteed Genuine Excelight EL1129L Original Equipment Lamp. Don't be Fooled by Knock-Offs!
- Related Products
- Installation / Manual
We are pleased to offer a complete selection of replacement lamps for all Excelight ultraviolet (UV) sterilizers.
Excelight #EL1129L replacement lamps are designed only for use in Excelights UV sterilizers. We do not recommend that you attempt to use Excelight replacement lamps in models made by other manufacturers.
Excelight #EL1129L is the replacement lamp for the following models:
- Excelight EL1129AK
Excelight #EL1129L Specifications
|Lamp Length||33 1/4"|
|Lamp Life||12 Months|
How to change a Excelight #EL1129L Lamp
Note: Do not touch the lamp or the quartz sleeve with your fingers. Handle by ends only or wear soft gloves.
- Unplug the system from the electrical outlet, turn off the water supply to the unit, and release the water pressure by opening a faucet and waiting until the water slows to a trickle.
- Carefully remove the lamp connector from the electrical end cap assembly to expose the top of the UV lamp. While holding the lamp base firmly, disconnect the lamp 4-pin connector by pulling off lamp. Warning: The lamp base can be very hot - be careful not to drop the lamp into the quartz sleeve as both are easily broken.
- Carefully slide the lamp out of the quartz sleeve and recycle.
- Loosen and remove both end caps. Roll back the o-rings at both ends and remove. Carefully extract the quarts sleeve from the reactor housing. The quartz sleeve is very fragile and is easily chipped or broken - use extreme caution when installing or removing it from the reactor vessel. NOTE: Do not touch the lamp or quartz sleeve with your fingers as grease can reduce UV efficiency. Handle by the ends only or wear soft non-abrasive gloves.
- Clean the quartz sleeve with vinegar or a scale-removing product. (Lime Away, CLR)
- Examine the quartz sleeve o-rings. If they look worn or cracked, replace them and reinstall the quartz sleeve.
- Install new lamp by reversing the procedure described in item #2 above, being careful not to touch lamp with bare hands
- Slowly open shutoff valves and purge the air from the system.
- Ensure there are no leaks at the end caps before reconnecting the power to the system.
- Reset the UV Power Source. The Lamp Life Days (lamp change reminder timer for models built after February 2011) is reset by disconnecting the UV power source from the AC power supply, waiting for 15 seconds and then reconnecting the AC power supply with the push button depressed until the screen displays “rSEt” followed by a short audible beep, the number “365” shows on the screen indicating that the reset was successful. (For models prior to February 2011 a three seconds beep indicates the successful power source reset)
Excelight EL1129L Replacement UV Lamp Reviews
There are currently no reviews for this product.
Be the first to write a review.